## Optical Loss Budget Calculation

On 21/Mar/2019, I wrote an introductory article on the “Optical Loss Budget” (http://www.claritytreinamentos.com.br/2019/03/21/optical-loss-budget-an-introduction/), where I present what an optical loss budget is and what’s its purpose. In this article, we will address how to calculate it.

To recall, the “optical loss budget” is a calculation performed to estimate what will be the total attenuation of a fiber optic link even before it is installed. Among its purposes, we can emphasize two:

• Verify that the optical link being designed meets the requirements of the applications that will run on it. If the calculated loss budget is greater than the loss margin allocated for the cabling of the intended application (e.g. 10GBASE-SR), the link may show data loss and even “go down”;
• Establish a threshold that will be used during the performance of acceptance tests of the installed link. When testing the link with a PMLS (power meter + light source), if the measured attenuation is greater than the project’s loss budget, then we will know that something has failed during installation: the material and/or the labor were less than reasonable.

But how to calculate the optical loss budget? First, we must know exactly which optical components will be used in the link. If possible, know the exact brand name and model. Usual components are:

• Fiber optic cable
• Connectors
• Splices
• Splitters
• Other passive components (e.g. taps and attenuators)

Next, we must determine the loss (attenuation) that each of these components will present when installed on the link. This information can be obtained from the technical specification sheets of the selected components. Caution: the attenuation may be different depending on the wavelength of light used.

The calculation must be carried out at all wavelengths intended to be used in the link. As a minimum, test:

• multimode fibers in wavelengths 850 nm and 1300 nm;
• single-mode fibers in wavelengths 1310 nm and 1550 nm.

If the part numbers of the components are not yet known, use standard market values or values specified by national or international cabling standards.

Examples of standard attenuation values established by ISO/IEC 11801-1:2017:

• Coupled connectors:                       0.75 dB
• Splice:                                             0.3 dB
• Multimode fiber OM1 thru OM4: 3.5 dB/km (850 nm) and 1.5 dB/km (1300 nm)
• Multimode fiber OM5:                   3.0 dB/km (850 nm) and 1.5 dB/km (1300 nm)
• Single-mode fiber OS1a:                 1.0 dB/km (1310 nm and 1550 nm)
• Single-mode fiber OS2:                   0.4 dB/km (1310 nm and 1550 nm)

We also need to know the total length of the complete link, in kilometers. That is because the loss of the “fiber optic” component will be proportional to its length (so the loss is given in “dB/km” as seen above).

Based on this information, we add all the values for the link to obtain its loss budget, in decibels (dB).

Example 1: A 3,000 m link made of OS2 single-mode fiber, terminated in pigtails spliced at both ends inside optical trays, whose connectors will be coupled to the front panel adapters. There will be a splice in the middle of the link:

Optical fiber loss: 3 km X 0.4 dB/km = 1.2 dB

Connector loss: 2 X 0.75 dB = 1.5 dB

Splice loss: 3 X 0.3 dB = 0.9 dB

Loss budget (1310 nm and 1550 nm): 1.2 + 1.5 + 0.9 = 3.6 dB

Example 2: A 200 m link made of OM3 multimode fiber, terminated in field polished connectors at both ends, coupled to the front panel adapters. No splices used:

Optical fiber loss @ 850 nm: 0.2 km X 3.5 dB/km = 0.7 dB

Optical fiber loss @ 1300 nm: 0.2 km X 1.5 dB/km = 0.3 dB

Connector loss: 2 X 0.75 dB = 1.5 dB

Loss budget @ 850 nm: 0.7 + 1.5 = 2.2 dB

Loss budget @ 1300 nm: 0.3 + 1.5 = 1.8 dB

As already mentioned, the values obtained should be compared to the applications specifications and to the values measured during the certification of the installed link.

If the measured value is greater than the calculated loss budget, check the installed material, the fiber route, the cleaning of the connectors and the quality of the splices. If necessary, use an OTDR to find the locations that exhibit losses above the expected.

If you found this post useful, share it, forward it to someone who might also find it useful.

See you next time.

Marcelo Barboza, RCDD, DCDC, NTS, ATS, DCS Design, Assessor CEEDA
Clarity Treinamentos
marcelo@claritytreinamentos.com.br

Marcelo Barboza, Structured Cabling instructor since 2001, graduated in Mackenzie University, has more than 30 years of experience in IT, member of BICSI, member of the ABNT/COBEI Committee of Studies on Structured Cabling (Brazilian Standards organization), certified by BICSI (RCDD, DCDC and NTS), Uptime Institute (ATS), and DCProfessional (Data Center Specialist – Design). Authorized instructor for selected courses of DCProfessional, Fluke Networks and Clarity Treinamentos.

## Optical Loss Budget – An Introduction

When designing a fiber optic link, how to ensure that there will be enough light for the application to work? Or, after installing the optical link, how to ensure that the material has of good quality and that the workforce used in the installation followed all the recommendations and good practices?

Each application (or physical network protocol, such as Ethernet, for example) for fiber optics establishes a maximum attenuation (or loss) in the channel for it to work without performance degradation. If the channel attenuation is higher than the expected, the bit error rate (BER) begins to increase, causing network slowdowns and eventually dropping the link.

Each optical component bought and installed must also have a maximum expected loss, defined in structured cabling standards. When acquiring and installing optical links, we should know what this loss is, so we can compare it to the measurements performed at the time of network certification. If the measured loss is greater than expected, whether the material acquired is not so good, or the manpower used in the installation did not follow the normative recommendations and the respective suppliers. In this case, the link may not be able to receive the extended warranty from the manufacturer.

It is precisely for this that there is such a thing as the “optical loss budget”, a calculation of how much loss an optical link should present, at maximum, to ensure the quality of the installation and the operation of the network.

See you next time!

Marcelo Barboza, RCDD, DCDC, NTS, ATS
Clarity Treinamentos

## Diferenças entre as formas de diafonia NEXT e FEXT

Neste artigo, vamos explicar o conceito dos parâmetros de diafonia/crosstalk NEXT e FEXT para cabeamento em par trançado e ressaltar suas diferenças.

O “par trançado” é um dos meios físicos mais utilizados nas instalações de cabeamento estruturado. Popularmente conhecido como “UTP” (embora algumas vezes seja composto por cabos blindados, e UTP se refira apenas aos não blindados), hoje permite a transmissão de dados a velocidades de 10 gigabits por segundo ou mais em enlaces de até 100 metros.

Mas, nem tudo são flores. Se não forem utilizados produtos de boa qualidade, ou se o procedimento de instalação não for corretamente seguido, problemas podem ocorrer. É por isso que, após a instalação, são realizados testes de certificação. São diversos testes, mas neste artigo abordaremos dois deles, o NEXT e o FEXT (para entender estes e outros testes, veja meu vídeo abaixo). Vocês sabe o que são eles? Quais as semelhanças e as diferenças entre eles?

## Diafonia

Ambos são parâmetros que medem a “diafonia” (“crosstalk”, em inglês, abreviado como “XT”), ou seja, a interferência eletromagnética que o sinal trafegado por um par de fios trançados provoca em outro par do cabo. Qual o problema da diafonia? Por que ela é indesejável?

Cada par de um cabo interliga um equipamento transmissor (TX, que está em uma extremidade do cabo) a um equipamento receptor (RX, na outra extremidade do cabo), ambos componentes de equipamentos de comunicações, como uma placa de rede ou porta de switch, por exemplo.

Só que em uma transmissão de rede, pelo menos dois dos pares do cabo são utilizados simultaneamente. Em uma transmissão Ethernet a 1 Gb/s (ou mais), são utilizados os quatro pares do cabo. Ou seja, dois ou mais TX transmitem simultaneamente para seus respectivos RX.

Agora que já sabemos o que é diafonia e como ela pode afetar a transmissão, vamos perceber que há dois tipos de medições realizadas de diafonia: NEXT e FEXT.

## Introduzindo o NEXT e o FEXT

O NEXT (near-end crosstalk) mede a diafonia que afeta o RX que está localizado na mesma extremidade do cabo (“extremidade próxima” ou “near end”) em relação ao TX que causou essa diafonia. Ou seja, o NEXT mede a interferência que um equipamento transmissor causa no cabo e acaba afetando a habilidade do próprio equipamento de entender sinais provenientes da outra extremidade do cabo.

Já o FEXT (far-end crosstalk) mede a diafonia que afeta o RX que está localizado na extremidade oposta do cabo (“extremidade distante” ou “far end”) em relação ao TX que causou essa diafonia. Ou seja, o FEXT mede a interferência que um equipamento transmissor causa no cabo e acaba afetando a habilidade do equipamento oposto de entender seus sinais.

Em português, o NEXT é chamado de “paradiafonia”, enquanto o FEXT é a “telediafonia”. Ambos medem as consequências do mesmo fenômeno, que é a diafonia.

## Testes de NEXT e FEXT

Ambos os testes devem ser realizados bidirecionalmente, ou seja, enviando-se sinal a partir de ambas as extremidades do cabo. Isso ocorre porque o próprio sinal indesejado (resultado da diafonia) sofre atenuação ao longo do cabo até chegar em algum RX. Por exemplo: um dano ao cabo que aumente a diafonia causará um NEXT muito mais elevado quando este for medido a partir da extremidade do cabo que estiver mais próxima a esse dano.

As medições de NEXT e FEXT são reportadas em combinações de dois pares ou somadas para todos os pares do cabo (“powersum”). A unidade de medida utilizada é o decibel (dB), resultado da comparação na intensidade do sinal transmitido com a do sinal indesejado recebido. O FEXT usualmente é reportado apenas após a computação da Perda de Inserção, resultando no ACR-F, mas isso já é um assunto para outro artigo!

Para saber mais sobre os testes realizados em enlaces de par trançado, não perca o curso SCE331.

Se achou este post útil, compartilhe, encaminhe a alguém que também possa achá-lo útil. Não deixe de se inscrever em meu canal do YouTube! Participe de meu grupo do Whatsapp e receba as novidades sobre meus artigos, vídeos e cursos. E curta minha página no Facebook!

Até a próxima!

Marcelo Barboza, RCDD, DCDC, NTS, ATS, DCS Design, Assessor CEEDA
Clarity Treinamentos
marcelo@claritytreinamentos.com.br

Sobre o autor
Marcelo Barboza, instrutor da área de cabeamento estruturado desde 2001, formado pelo Mackenzie, possui mais de 30 anos de experiência em TI, membro da BICSI e da comissão de estudos sobre cabeamento estruturado da ABNT/COBEI, certificado pela BICSI (RCDD, DCDC e NTS), Uptime Institute (ATS) e DCPro (Data Center Specialist – Design). Instrutor autorizado para cursos selecionados da DCProfessional, Fluke Networks, Panduit e Clarity Treinamentos. Assessor para o selo de eficiência para data centers – CEEDA.